- Cabling and Connection
- Error Messages
- Firmware and Drivers
- Operating System
- Options and Accessories
- Product Substitution
- Schneider Electric software
- Service and Repair
- Technical Characteristics
- Technical Documentation
What are the safety clearance dimensions for a LC1B range contactor switching with the DC voltage.
The safety clearance distances are as per the attached table. These values are given for AC voltage; however these values are same as in case of DC...
Can the TeSys range overload relays be used in DC application?
The overload relay with the bimetal technology (Thermal Overload) only can be used in DC application. Tesys LRD Range Tesys LRD thermal overload...
How to change page resolution in configured project of Vijeo Citect?
In order to change the resolution of the pages in Vijeo Citect project do following things: 1. Add the following INI parameter through Computer...
Is it possible to give continuous supply to the Shunt Trip (MX) coil of circuit breaker?
Yes, you can keep the supply ON continuously for the Shunt Trip coil (MX) of Circuit Breaker as new technology permits this without damaging the Shunt...
What are the minimum and maximum cable sizes recommended for use with TeSys D Star-Delta connection kits?
The minimum and maximum cable sizes recommended to be used with TeSys D Star-Delta kits are: Kit Minimum (Sq. mm) Maximum (Sq. mm) LAD91217 1 4...
Is it possible to install the rectangular sensor at the incoming side of the Masterpact ACB with Micrologic 7.0?
Yes, it is possible to install the rectangular sensor at the incoming side of the Masterpact Air circuit breaker (ACB). The earth leakage protection...
How to connect the Vigi Module with Compact NS MCCB?
Refer the Vigi Installation Guide for the instruction to connect the Vigi module on the Compact NS Moulded Case Circuit Breaker (MCCB). Caution: Before...
How to enable the Navigation Panel option in ProWorx32?
To enable the Navigation Panel option in ProWorx32, check the 'Enable Scrolling Navigation Panel' option in the properties window of ProWorx32 Software....
What are the different Communication Networks on which the Altivar 61 Drive can be communicated?
The different Communication Networks on which the Altivar 61 Drive be communicated are as follows: 1. Ethernet TCP/IP 2. Modbus/Unitelway 3. Fipio...
Which power phases are controlled by Altistart 01 Soft-Starter?
The power phases that are controlled by Altistart 01 Soft-Starter are as follows: In N1 Range of Altistart 01 Soft-Starter only 1 Phase is controlled...